UNITRONIC® LAN 200 Cat.5e
Ethernet cable for Category 5e/ class D - verfied up to 200 MHz
- LAN cables for structured building cabling according to EN 50173 and ISO/IEC 11801
- Mainly used where the terminal density is very high, e.g. for wiring office, administration and development buildings in the tertiary area (floor wiring).
- Cable length in tertiary area (horizontal area, floor) should not exceed a length of 100 m in accordance with the ISO/IEC 11801 and EN 50173 standards (90 m in cable duct + 10 m in working area)
- Transfer of digital and analogue data signals
- IEEE 802.3: 10/100/1000Base-T
IEEE 802.5: ISDN; FDDI; ATM
- Flame retardant acc. to IEC 60332-1-2
2170138: flame retardant acc. to IEC 60332-1-2 and IEC 60332-3-24
Norm references / Approvals
- LAN CAT.5e cables from Lapp Kabel for "Structured Cabling Systems” meet the requirements in accordance with EIA/TIA-568 and TSB36, as well as ISO/IEC 11801 or EN 50173 (Class D).
- Solid conductor
- U/UTP: no overall or pair screening
- F/UTP: foil screening as overall screening
- SF/UTP: braid of tinned copper wire and plastic laminated aluminum foil as overall screening
- outer sheath either as PVC or LSZH (color grey RAL 7035)
Classification ETIM 5
- ETIM 5.0 Class-ID: EC000830
- ETIM 5.0 Class-Description: Data cable
Classification ETIM 6
- ETIM 6.0 Class-ID: EC000830
- ETIM 6.0 Class-Description: Data cable
Minimum bending radius
- during installation: 8 x outer diameter
- Fixed installation: 4 x outer diameter
- 100 Ω ± 15%
- Operating temperature: -20°C to +60°C
- During installation: 0 °C to +50 °C
- Unless specified otherwise, the shown product values are nominal values. Detailed values (e.g. tolerances) are available upon request.
- Copper price basis: EUR 150/100 kg. Refer to catalogue appendix T17 for the definition and calculation of copper-related surcharges.
- Please find our standard lengths at: www.lappkabel.de/en/cable-standardlengths
- Packaging size: Coil 100 m; Drum (500; 1000) m
- Detailed data sheets are available upon request. Please specify the type/dimensions of the required cable.
- Photographs and graphics are not to scale and do not represent detailed images of the respective products.